Toyo condenser Guangdong brand condenser Dong ...
Shenzhen Toyo TY-02A acid and alkali resistant air-cooled ...
Air-cooled chiller / Toyo TY-12A air-cooled ...
Condenser | Toyo TYS-10 Shell and Tube Condenser | ...
Electroplating chiller / Shenzhen Toyo TY-02A air cooling ...
Condenser | Toyo TYS-12 Shell and Tube Condenser | ...
Chemical chiller / Toyo TY-15A box ...
Toyo chiller / Toyo chiller manufacturer / Toyo ...
Address No.8 Building, Longxi Third Industrial Zone, Longcheng Street Office, Longgang District, Shenzhen
、 如何正确选择冷水机？ 1. How to choose a chiller properly?
Toyo Refrigeration, a well-known service provider of Shenzhen chiller, said that the quality of the equipment can be viewed from the three major pieces of chiller. First look at the compressor, which is called the heart of the unit and is the most critical component. A good compressor should not only run stably, but also ensure good energy efficiency. Secondly, look at the evaporator and the condenser. The evaporator and the condenser play the functions of absorbing and releasing heat, respectively. A sufficient and appropriate heat exchange capacity can fully exert the efficiency of the compressor. If the heat exchange capacity of the condenser is insufficient, it will directly affect the cooling effect of the unit. In the summer, high pressure is likely to be high or even the chiller protection shutdown due to high pressure exceeding the standard; the heat exchange capacity of the evaporator is more important. The efficiency of the unit is low. If the unit is too small, the refrigerant cannot completely evaporate, and it returns directly to the compressor, causing liquid hammer and damaging the compressor, making the entire chiller unit unusable. Another important component is the expansion valve. The expansion valve is a flow regulating valve in the chiller refrigeration system. Its main function is to reduce the pressure of the high-pressure and normal-temperature refrigerant liquid when it passes through the thermal expansion valve to become a low-temperature and low-pressure refrigerant. The wet vapor enters the evaporator, and vaporizes and absorbs heat in the evaporator to achieve the purpose of cooling and cooling.
Pay attention to the following points when choosing a chiller:
1 ）冷水机组关键配件的选择。 ( 1 ) Selection of key accessories for chiller. Compressor is the main index that affects the performance of the shadow chiller. In the production process, many chiller manufacturers use poor quality products such as compressors to control the overall production cost, and even use refurbished compressors. It severely affects the later use efficiency of industrial chiller, causing continuous increase in energy consumption.
2 ）控制采购成本。 ( 2 ) Controlling procurement costs. Under the premise of ensuring the main energy of the chiller, purchasing a suitable industrial chiller product at a high cost performance ratio can achieve the purpose of reducing costs and meet the production needs of the chiller with minimal capital.
3 ）根据企业使用环境采购冷水机组。 ( 3 ) Purchasing chillers according to the environment in which the enterprise is used. Water quality and air quality have a certain impact on the operation of the chiller. You must tell the chiller manufacturer in advance about the water quality and air quality of the location of the enterprise.
、 安装冷水机的注意事项？ 2. Precautions for installing chillers?
、工业冷水机的调试要点？ 3. What are the key points of industrial chiller commissioning?
、使用冷水机的注意事项？ 4. Precautions when using chiller?
、如何维护及保养冷水机？ 5. How to maintain and maintain the chiller?
、冷水机系统运行检查项目有哪些？ 6. What are the inspection items for the operation of the chiller system?
、冷水机常见故障及解决办法 7.Common faults and solutions of chiller
l Chiller compressor does not start
l Chillers are not cooling
l Air-cooled chiller fan does not run
l Trip on chiller start
l The condenser is suddenly cold and hot
l Compressor vibration and noise
、如何正确选择冷却塔？ 8. How to choose the correct cooling tower?
、冷却塔安装时应注意什么？ 9. What should I pay attention to when installing cooling towers?
、冷却塔的清洁工作包括哪些？ 10. What does the cleaning work of the cooling tower include?